Metallurgical Failure Analysis
Our client experienced a rupture failure on a 16-inch OD by 0.250-inch WT API 5L X42 electric resistance welded longitudinal seam pipe. The pipeline was installed in 1947.
The client called on ENTRUST Solutions Group to perform a failure analysis on the rupture and to determine the root cause of the failure.
ENTRUST Solutions Group performed a formal metallurgical evaluation on the pipe rupture failure that included a visual examination of the fracture and the failed pipe; nondestructive examination of the internal and external pipe surfaces; and scanning electron microscope (SEM) evaluation. In addition, the engineers documented the fracture dimensions, including pipe wall thickness along the fracture surface, and the circumferential position of the electric resistance weld longitudinal seam. They also visually examined the pipe for internal and external corrosion; conducted a metallographic examination of the fracture surface, including preparation and examination of metallographic cross sections under a light microscope; and completed a chemical analysis.
The team’s mechanical testing included:
Upon completion of the project, ENTRUST delivered a report showing the cause of the rupture was high-pH stress corrosion cracking.